In the following we show a schematic diagram of a
cooling tower in the context of a steam power plant:

**mass flow:**

Referring to the diagram above the mass flow rate of the makeup water is given by the difference in specific humidity ω at the inlet and outlet air streams multiplied by the mass flow rate of the dry air. Thus the mass flow balance equations for the cooling tower become:

**energy:**

Since no work is done and no heat transfered externally, the cooling tower energy equation reduces to an enthalpy balance equation. Combining the mass flow equations with the energy equation leads to the final equation relating the mass flow rate of the dry air to the circulating cooling water of the condenser, as follows:

The mass flow rate of the liquid water at stations
(3) and (4) is normally provided from the condenser energy equation
of the steam power plant. Recall from **Chapter
10a** that the specific humidity ω is
related to the various pressures and the relative humidity φ by the
following relations:

The pressure P_{v}
is the partial pressure of the vapor, P_{g}
is the saturation pressure at temperature T, and P is
the total pressure (air + vapor), usually taken as one atmosphere
(101.325 kPa). In **Chapter
10b** we saw how all of these relations can
be most conveniently evaluated graphically on a **Psychrometric
Chart**. Notice that we have extended the
moisture specific humidity range on this chart from 30 to 40
grams/kg-air in order to accomodate the extremely high humidity
normally encountered at station (2), which is the reason why we
normally see a cloud above the cooling tower.

Note that the enthalpies of the vapor (h_{1}
and h_{2}) and those of the liquid (h_{3}, h_{4},
h_{mu}) can be conveniently evaluated as follows:

The temperature T is in degrees Celsius, and the
specific heat capacity of dry air C_{P} is
approximately 1.00 [kJ/kg°C] and that of liquid water approximately
4.18 [kJ/kg°C]. In the above analysis we have assumed that the
temperature of the makeup water T_{mu}
equals the temperature of the cooled circulating water
T_{3}. Alternatively
the values of enthalpy for the vapor (h_{1}
and h_{2})
can also be conveniently read directly from the Psychrometric Chart.

**Solved
Problem 10.5 - ****Cooling Tower for the
Supercritical Steam Power Plant for Athens, Ohio**

**Problem
10.6 - ****Cooling Tower for the Cogeneration
Steam Power Plant for Ohio University**

______________________________________________________________________________________

Engineering Thermodynamics by Israel
Urieli is licensed under a Creative
Commons Attribution-Noncommercial-Share Alike 3.0 United States
License